TEK E-INDUSTRY GRP CO.,LTD Address: 126,Tianma Rd, Qinxiyang Industry Zone, Fuan, Fujian, China P.C: 355000 Tel: 0086-593-6797136 0086-593-6338998 Fax: 0086-593-6797138 Mob: 0086-18033963558 Website:http://www.tek-cn.com E-mail: firstname.lastname@example.org email@example.com MSN: firstname.lastname@example.org Skype: tek-tema Yahoo MSG: tema liu Trademanager: cntek QQ: 704107616
MS Stainless Steel Horizontal Single-stage Centrifugal Pump
Definition of model MS 250 / 1.5 MS stainless steel horizontal single-stage centrifugal pump 250 Rated flow (1/min) 1.5 Rated power(kW) Application 1、Pressurization and pumping of industrial and civilian clean water of other liquids; 2、Water treatment; 3、Water circulating system; 4、Agricultural irrigation; 5、Other fields. Structure features 1、MS Series of pump is single-stage centrifugal pump and features axial suction and radial discharge ; 2、Compact structure ,The pump is directly connected with the motor ,coaxial installation ; 3、Convenient installation ,screw thread water inlet and outlet ; 4、Light weight ,thin plate pressing structure for main parts and components ; 5、Corrosion resistance ,components passing the flow use AISI 304 or AISI 316 stainless steel. Pumping liquids 1、thin ,clean ,non-flammable and explosive ,not containing the liquid with solid particle and fiber ; 2、Able to transmit light corrosive medium (have a bearing on the content of chloride ion in the medium ,thickness of acid or alkali ,whether generate corrosion on the rubber and mechanical seal materials ); 3、The density of transmitted medium is less than that of clean water ,viscosity close to that of water .Otherwise the motor of large power is required. Operating condition 1、Liquid temperature :-10℃~+85℃ 2、Ambient temperature :up to +40℃ 3、Altitude :up to 1000m 4、Max. pressure of the system is 8 bar Installation requirements 1、The pump shall be fastened on the stable horizontal base ; 2、The installation of the pump shall ensure that the pump will not be influenced by the tension of the pipeline ; 3、The pump shall be installed on the ventilating and anti-freezing place to ensure normal operation of the motor ; 4、Electric wiring device shall guarantee that the pump will not be damaged by lack of phase , unstable voltage ,current leakage and overload.